The F52F Return Grille Electronic Air Cleaner is wall or ceiling mounted in the main return air duct of a central forced air heating, cooling, or ventilation system. It captures a significant number of the airborne particles (0.5 microns and larger) from the air circulated through the cell(s).
Removes airborne particles from the air circulated through it.
Electronic cells can be washed easily.
Neon light shows that air cleaner is operating.
Wiring consists of simply connecting air cleaner to power source.
Solid state power supply is energized by an airflow switch; no interconnection to the fan system is required.
Solid state power supply is self-regulating and maintains peak efficiency during a wide range of cell dirt loading conditions.
Automatic interlock switch disconnects power when unit is opened.
Use with optional W8600F Electronic Air Cleaner Monitor (ordered separately) to monitor air cleaner performance.
High Efficiency Electronic Air Cleaner
20 in. x 12 1/2 in.
508 mm x 318 mm
Airflow Max.-Capacity (cfm)
Airflow Max.-Capacity (m³/hr)
Efficiency ratings are based on American Society of Heating, Refrigerating and Air-Conditioning Engineers Standard 52.2-1999.
Efficiency ranges are defined for small particles, E1=0.3 to 1.0 microns; medium particles, E2=1.0 to 3.0 microns; and large particles, E3=3.0 to 10.0 microns.